Tulameen Community Water System
June 14, 2018 Summary of Proposed Water System Status for Tulameen
Some questions are still arising from the proposed water system for Tulameen that was brought to the community in late 2016. In order to clarify some of the reasoning for actions or inactions and the current status of the conceptual project, the following information is being provided.
The public meeting date was selected for November 29th, 2016 based on availability of the required RDOS staff. We were aware it may not have been the most convenient date for everyone which is why information was sent out via email and included on the website.
The details on the potential water system were only at a very preliminary or conceptual stage and did not provide specific details on any aspect of the proposed works.
The meeting and information provided for November 29, 2016 was intended to gauge the community’s desire to have the RDOS spend additional staff time and funds to investigate the potential of getting a water system designed.
There is not a current service area so any wages and study work was coming directly out of contingency funds from the Electoral Area H budget. Gas Tax funds could not be used unless a capital project was guaranteed to occur – i.e. putting water pipes in the ground.
I believe the details you were seeking on the water system layout had not been developed for this initial meeting. The layout shown was a very high level to determine if there was adequate interest to move forward.
If a positive response was received the RDOS was going to move forward with the predesign stage to prepare improved cost estimates and detailed layout of the system.
An overwhelming negative response was received, so RDOS staff put the Tulameen water system project to the side to focus on more critical issues and projects.
The RDOS engineering staff had a very busy 2017 with numerous approved grant projects with very tight deadlines as well as several regulatory requirements to meet.
The negative response plus the large demands on the engineering team, resulted in the June meeting for Tulameen being cancelled and thus no additional information was produced.
We received several people requesting staff to continue moving forward however, due to the low overall community support, this project was put aside for the remainder of 2017.
The potential of adding a water system in Tulameen has been asked about several times over the past decades, specifically an engineering report was prepared in 1995 and updated in 2005, and again in 2008.
During each of those times, the community ended up being opposed to moving forward due to the high costs of installing a new system. Hence the work was stopped at this preliminary stage each time.
When enough residents request the RDOS to look into the water system potential, the RDOS has responded each time. Unfortunately, the public opinion at large has been negative thus resulting in additional work being stopped.
If further work is to be completed in the future, a significant amount of public support will be required and the community will be engaged at the early stages again.
Liisa Bloomfield, P.Eng., PMP ● Engineering Supervisor
Regional District of Okanagan-Similkameen
101 Martin Street, Penticton, BC V2A 5J9
p. 250.490.4229 ● tf. 1.877.610.3737 ● f. 250.492.0063
June 10, 2017 Tulameen Public Information Meeting - Cancelled
The scheduled June 10, 2017 Tulameen Public Information Meeting is being postponed until a later date when more technical information can be provided. Further updates will be provided as they become available.
The RDOS has booked the Tulameen Community Hall for June 10, 2017 from 10 am to 2 pm for a Public Information Meeting on the Proposed Water System for the Community of Tulameen.
Newsletter - Keeping the Community Informed on the Proposed Water System for Tulameen
November 2016 Feedback Survey Results
The RDOS sent out 375 surveys and received back 147 surveys. Results of question asked below:
Would you be interested in hooking up to a community water system?
The above Feedback Survey results were collected from the residents when asked about a domestic water system for the community of Tulameen.
We found from the comments submitted and the Yes votes that residents showed more interest for a fire protection system more so than a domestic water system.
November 29, 2016 Tulameen Public Information Meeting - Proposed Fire Flow and Water Distribution System Meeting
A Public Information Meeting was held at the Tulameen Community Hall on November 29, 2016 where RDOS staff, engineering consultants and Area H Director, Bob Coyne, discussed a proposed Tulameen Water Distribution System. The intent of the preliminary informal meeting was for the Electoral Area Director to be able to gauge the interest from property owners for a proposed establishment of a Local Service Area for the purpose of installing a Tulameen Community Water System to deliver fire protection and potable water to the community. The meeting was very well attended by local residents and several property owners who travelled as far away as the Lower Mainland and Lake Country.
Several informational story boards were showcased that outlined the preliminary engineered design of the water system. Additionally, a suggested phased approach for the installation of the infrastructure and preliminary costs attributed to each phase was identified. A subsequent effect of annual costs to the property owners was also noted for these phases.
The project is at the infancy stage of discussion. The next step, with Director approval, would be to perform a hydrological study, a detailed design of the community water system with attributable potential costs to the property owners and communicate these findings back to the community. The timeline for the next Informational Public Meeting would be in the Spring/Summer of 2017 when the majority of the property owners are in the area to attend.
Message from Director Coyne:
" I would like to thank all the people from Tulameen that attended the Public Information Meeting. I was very pleased to see the number of people that attended, some came from the coast, the Okanagan and lots of locals.
There were lots of positive comments and lots of questions. We did our best to answer as many questions as possible. There were questions we couldn't answer as this project is just in the early planning stages. We had two engineers involved on hand to answer questions and explain how the system could be built.
Please fill in your survey and add any comments or concerns you may have and send it in to the Regional District of Okanagan-Similkameen, email@example.com. This is very important as this is how we are going to gauge the community interest in the proposal.
Again thank you to everyone that attended the meeting or sent in their questionnaire."
All information presented at the November 29th meeting is available to view below by clicking on the supplied links. The RDOS kindly asks the property owners to submit their completed survey back to the RDOS for processing by December 14, 2016.
The proposed water system would provide domestic and fire suppression service for the Community of Tulameen. Proposed works are illustrated on Figure 2 and would comprise:
- Water supply from drilled wells located at the south-western extents of the community.
- A reservoir on the hillside area on the west side of the community. The reservoir would be sized for balancing storage during peak demand periods and fire protection.
- Looped water distribution system comprising 150mm and 200mm water mains with hydrants spaced consistent with accepted municipal standards.
A phased construction plan has been proposed for this project. Ideally, sufficient funds would be available to construct a water supply well, a reservoir and the water distribution system in the community core area. Infrastructure assistance programs could then be targeted to assist with build-out of the full water system after the initial phase has been completed. The current phased plan for this project is described as follows:
Phase 1 – Water Supply Wells and Community Core Area Water Distribution System
Components are illustrated in red on Figure 2 and would comprise:
- Water supply wells located on crown land near the Tulameen River at the south-western extents of the community. To supply the design maximum day demand, two wells each having a capacity of 15.6 L/sec (250 USgpm) are proposed.
- A water treatment building having a footprint area of about 20m² (200 ft²) enclosing hypo chlorination system, flow meter, electrical for the pumps and controls.
- Assuming that Phase 1 of the water system may not include the reservoir, hydro pneumatic tanks to control the pumps would be provided in the water treatment building.
- The water distribution system comprises 380m of 150mm main from the proposed well site to Third Street, 200m of 250mm main on Third Street to Otter Avenue, and 210m of 200mm water main on Otter Avenue terminating in a fire hydrant at the fire hall. To the greatest extent practical, distribution mains would be located in boulevard area to minimize asphalt restoration requirements.
- The water distribution system would provide service to about 38 properties including the service station, library, community hall, motel and the fire hall.
Without a reservoir, Phase 1 of the water system would have the capability of providing fire flow of about 25 L/sec (400 USgpm) representing the combined capacity of the two proposed well pumps. This level of fire flow is not consistent with FUS guidelines, but would provide the community fire department with a reliable water source for fire suppression purposes except in the event of a power failure.
Phase 2 – Water Reservoir and Supply Main
No topographic information is available for the reservoir sites therefore the location as shown in Figure 2 is approximate. Components of Phase 2 are illustrated in green on this figure and would comprise:
- reservoir having a capacity of 710m3 (190,000 USgallons).
- reservoir appurtenance including level controls, provisions for a mixer, drain, overflow, fencing, etc. The reservoir appurtenances would be subfed from water treatment building.
- 150mm dedicated water supply main to the reservoir and a 250mm supply main from the reservoir to the community. The dedicated supply main offers the flexibility to provide disinfection with contact time should bacteria or virus become an issue in the groundwater.
Phase 3 – Water Distribution System
Phase 3 is shown in Figure 2 as the remainder of the water distribution system. While designated as Phase 3, the water distribution system could be built in multiple phases as available capital funds permit. Components for this phase are illustrated in blue on Figure 2.
True Consulting, Figure 1 Tulameen Area Individual Well Sampling Locations
True Consulting, Figure 2 Proposed Phased Plan Tulameen Community Water System
Reservoir Design Option